FULLY AUTOMATIC SUBMERSIBLE PUMP STARTER CONTROL PANEL USING MAGNET SENSOR BASED FULLY AUTOMATIC WATER LEVEL CONTROLLER WITH HIGH / LOW VOLTAGE + OVER LOAD + CURRENT BASED
DRY RUN PROTECTION AND RUN TIME OVER TIMER
Fully automatic submersible (open well) pump starter control panel with magnet sensor based water level controller. Control panel for automatic turn ON & OFF of open well submersible pump in the under ground tank.
There is a facility to add ‘RUN’ capacitor in the panel.
LEVEL CONTROLLER+PUMP PROTECTION
MAKES YOUR PUMP AUTOMATIC. PUMP TURNS ON AND OFF AUTOMATICALLY ACCORDING TO TANK LEVEL. FOR LEVEL SENSING MOST ADVANCE MAGNET SENSOR TECHNOLOGY IS USED WHICH IS RUST FREE, NO DANGER OF ELECTRIC SHOCK AND NO SALT DEPOSITION.
HIGH: When input supply voltage exceeds above SET voltage, it cuts off the mains supply to protect
your appliances. High voltage cut off level can be programmed (set) by user himself.
LOW: When input supply goes below SET voltage, it cuts off the mains supply to protect your appliances. Low voltage cut off level can be programmed (set) by user himself. OVERLOAD: It protects your pump from burning due to overload. Overload cut off level can be programmed (set) by user himself.
CURRENT BASED DRY RUN PROTECTION: Prevents pump from running dry without water and
thus burning out. Dry run off level can be programmed (set) by user himself.
AUTO START: When supply voltage becomes normal, electric supply will be turned ON automatically.
DELAY START TIMER: When supply voltage becomes normal, the electric supply to the output turns ON after a delay of 10 seconds, which protects the motor in case of frequent voltage fluctuations.. AUTO
STOP SIREN: In case of any fault trip condition, a buzzer will sound only for 5 seconds.
AUTO / MANUAL SWITCH: In AUTO mode, the pump will automatically turn ON and OFF by
sensing the water level in the tank, whereas in MANUAL mode pump has to be turned ON and OFF
manually by push buttons only and water level in the tank will not be checked.
RUN TIME OVER TIMER: If pump remains ON for a time greater than the programmed time, then system will trip in “RUN TIME OVER”. In this way, even in a sensor fail condition, pump will not remain ON continuously.
There are no reviews yet.